- DCS handles more nos of I/Os rather than PLC.
- PLC is faster system than DCS.
- DCS can handles handsome quantity of I/Os so that can be used for total plant automation. Where as PLC has own limitations so it generally used for small but for important(Safety point of view) units, like boiler automations, Make-up compressor automations Etc.
- In the above mentioned case the these PLC’s can be get connected with the DCS with the help of soft link. Generally this is used to make alert to both the operator.
- As I heard the PLC used to handle the DI/DO signals so it can take fast actions. Some of the time it is used to handle few nos of AI/AO.
- DCS & PLC’s speed depends on the scan rate of I/Os.
- For both the system Marshalling panels, Consoles and other faculties of Ethernet Etc can be used according to the need.
- According to the Cause and effects diagrams the System programmer assigns the control action block into the system, we can call them as memory assigning.
Check the following articles
Difference between DCS and PLC systems
> DCS versus PLC
DCS stands for “Distributed Control System”. DCS’s were designed to control processes, not discrete operations. As such, a large number of the inputs and outputs are analog like a 4-20mA signal or 0-10V signal.
In Literary meaning, a Distributed Control System (DCS) refers to a control system usually of a process or manufacturing system, in which the controller elements are not central in location (like the brain) but are distributed throughout the system with each component sub-system controlled by one or more controllers. Process plants used to have long series of panel mounted Single Loop Controllers (Analog/PID controllers).
PLC stands for “Programmable Logic Controller”. Historically a PLC was in discrete control of manufacturing processes. Whole discrete logic used to be implemented with relay circuitry. Most of the inputs and outputs for discrete control are binary, meaning they have only two states: On and Off.
What are attributes and characteristics which differentiate the PLC system from the DCS. There have been claims and counter claims from different manufacturers that their system is DCS or PLC.
The topic has remained under debate for long, and especially today when we have already entered into new era of Hybrid Distributed Control Systems, it has become increasingly difficult to select and differentiate the advantages and drawbacks one can get from different systems.
There are few similarities and dissimilarities which I would like to mention here:
DCS are designed or made available to the user in a way that only configuration in form of a Functional Block has to be carried out unlike PLC, where complete programming has to be implemented using any one of the different languages available in the system.
Now, Functional Blocks are also available in the PLC systems, which really makes it comparable to DCS.
When DCS started emerging in the market, idea was to supply DCS with whole bunch of hardware and software packages including for Human Interface, necessary for the complete automation of the plant, thus facilitating Single Point Configuration in terms of database and communication possible in general. Additionally, Human Interface does not need separate communication package i.e DDE server, to communicate with the controller. DCS includes higher levels of application software for regulatory and batch control.
In case of PLC systems, PLCs were not supposed to be in packages but competition with DCS vendors forced the PLC manufacturers to offer necessary all other softwares and packages.
Many DCS are designed such that it is possible to configure cycle time for each Functional Block. Thus DCS system takes care of cycle time scheduling of the Functional Blocks which are the basic execution units. This is one of the reason that overall scan time of the DCS is comparatively higher than the PLC system.
This functionality has been introduced in PLC systems(s) in some form as well.
A DCS has inherently multiple processor capability thus making the functionality distributed across a network. In a typical multi-processors (multi-node) DCS architecture, Engineer has to put in less efforts for inter-communication of the processors or one controller can easily access the Tag(s) from the database of the other .i.e the input of FB in one controller can be output of FB of the other controller.
This is possible now in PLC but more efforts have to be put in.
DCS programming is centered around configuration of Functional Blocks and discrete logic is implemented in DCS using FBs, thus making the DCS inherently an analog control system (although ladder programming is also possible in some of the DCS also). PLCs were programmed using Ladder/Relay language , before arrival of IEC 1131-3 standard and Analog control was incorporated inside Ladder inside Ladder Logic using special FBs. This is probably the reason we look at some of the process plants that process (Analog) control is done by the DCS, while emergency control (Discrete Control) is implemented by PLC based systems.
PLCs are still being used at RTU stations because of their simple, small and cheaper architecture as well as engineering (typically the RTU application) instead of big DCS. DCS have been used as the central system in a SCADA network. In a typical SCADA scenario, one DCS is connected to many PLCs systems.
Being Discrete in nature, PLC was natural choice of manufacturer and end-user to apply it for safety system. This led to production of specialized safety system conforming to SIL3 certification in accordance with ANSI / ISA 84.00.01-2004.
Today, a lot has changed, it is difficult to distinguish between two systems in terms of its main features. Differences between the two has virtually vanished due to Programming / Configuration language standard IEC-61131.The functionality of the PLC has evolved over the years to include sequential relay control, motion control, process control, distributed control systems and networking. However, in major industrial areas and structure markets, it is practice to deploy DCS for process control and PLC based system for safety control. Perhaps, for a large install base like more than 1000 I/Os system, cost of installation, addition and maintenance per I/O is less in case of DCS system.
Now, more important is cost, application, system integrity, reliability, maintainability, historical logging / intelligent statistics and learning / training. How much support is available from the vendor for the operation matters most to the operator now.
This has resulted into ‘Solutions Packages’ by vendors to their customers instead of simply offering individual products. It is DCS or PLC, must come in a solution package. More and improved System functionalities have made these system more complex which require strong integration between the operator /user and the manufacturer.
Few vendors also introduced Hybrid DCS / PLC system or transformed their PLC based system into DCS by incorporating similar features. DCS vendors have now introduced packages for Asset Optimization and management which seamlessly integrate with their systems. It is difficult to say which system to select ? It varies from user to user as discussed above. It is End-User who has to have all knowledge and courage to take responsibility of his system in totality…
- DCS provides MMI(Man machine interface).
- DCS pertains advance control strategies like sampling, fuzzy logic, neural network for artificial intelligence.
- DCS has integrated PID & analog control loops.
- DCS supports advance peripherals like keyboard, graphic displays, trend displays, group displays & overview displays.
- DCS possess various hierarchy of levels under which safety, production specification, energy conservation and management level requirements could be met.
- DCS integrated with PLC reduces size & complexity.
The differences between DCS and PLC are: DCS (Distributed Control System) is a CONTROL SYSTEM that works using several controllers and coordinates the work of all these controllers. Each controller is handling a separate plant. This controller is referred to the PLC.
The PLC (Programmable Logic Controller) is a CONTROLLER which can be re-program back. If the PLC is only a stand-alone and not combined with other PLCs, it is called as DDC. It means PLC is a sub system of a large system called DCS.
What’s difference between PLC and DCS by its definition
PLC is a controller or processor that can be programmed (programmable) whose function is to run (execute) logic functions. Logic means the discrete / sequence function is usually handled by the relay. From the beginning of the vendors who carry the name of the PLC is engaged in the business discrete / sequence control.
Regardless of the distributed control system (as opposed to the DDC = Direct Digital Control) is categorized as a DCS. In DDC all system controls are done in the central processor so that if it failed, the entire control plant will also failed. DDC is mostly used as a Regulatory Control. And from the beginning vendors that carry the name of DCS is to use the product as a regulatory control.
Different in functionality means that the DCS and PLC can not be implemented on the same application.
- DCS is not a large PLC. Because system architecture of DCS and PLC are different.
- DCS is not PLCs that integrated into one large system. “Controller” in the PLC is more intended as a “Logic Controller”, while “Controller” in the DCS is more intended as a “Process Controller”.
- Both DCS and PLC is a configurable and reconfigurable.